dixell. DEFAULT SETTING VALUES. تا تا تست ه تا تن تا نا م ع. XR60C signals and records temperature alarms, together with their duration and max. View and Download Emerson Dixell XR60C installing and operating instructions online. Digital controller with defrost and fans management. Dixell XR60C. Dixell Srl reserves the right to change the composition of its products, even without or faulty operation send the instrument back to the distributor or to Dixell Srl.
|Published (Last):||19 February 2004|
|PDF File Size:||13.59 Mb|
|ePub File Size:||10.61 Mb|
|Price:||Free* [*Free Regsitration Required]|
Dixell Srl reserves the right to change the composition of its products, even without notice. In case of applications in industrial environments, the use of mains filters our mod. Unidrive hs series; unidrive m series.
Other parameters are used to control the.
Then the instrument displays the temperature once again. Push and immediately release xf60c SET key: To see the last temperature alarm happened; in programming mode it browses the. Push and immediately release the SET key or wait for 5 seconds to.
To see the kind of alarm, the max min. Page of 4 Go. Consider the maximum current which can be applied to each relay see Technical Data.
Flexible machine integration through communications 50 pages. Fit the probe where it is not accessible by the End User. Got it, continue to print. To print the manual completely, please, download it.
An additional parameter “FSt” provides the setting of temperature, detected by the evaporator. To confirm the operation, the “rSt” message starts blinking and the normal temperature.
XR60C – AS Catering Supplies
To display target set point; in programming mode it selects a parameter or confirm an. At the end of defrost dripping time is started, its length is set in the FSt parameter. Each LED function is described in the following table.
The instrument is fully configurable.
electronic controller DIXELL XR60C-0N1C0 | horecatiger
Do not expose to water or moisture: On the display the following message is shown: Hold the SET key pressed for more than 3s, while the recorded alarm dicell displayed. Check the supply voltage is correct before connecting the instrument. Digital controller with defrost and fans management. Don’t have an account? The instrument is didell with screw terminal block to connect cables with a cross section up nPS Pressure switch number: The instrument must not be opened.
This manual is part of the product and should be kept near the instrument for easy and quick.
electronic controller DIXELL XR60C-5N3C1 mounting measurements 71x29mm 230V voltage AC NTC
Don’t show me this message again. In dixelll of fault in the thermostat probe the start and stop of the compressor are timed through. Universal variable speed ac drive for induction and permanent magnetmotors pages. By pressing ‘print’ button you will print only current page.
Comments to this Manuals Your Name. The fan control mode is selected by means of the “FnC” parameter:. The instrument shall not be used for purposes different from those described hereunder. Ensure that the wires for probes, loads and the power supply are separated and far enough. In case of failure or faulty operation send the instrument back to the distributor or disell “Dixell.
This is used to make sure circulation of air only. This manual also for: Add to my manuals Add. Enter text from picture: This function managed by the Fct parameter is designed to avoid short cycles of fans, that. After defrost, there is a timed fan didell allowing for drip time, set by means of the “Fnd”. Two defrost modes are available through the “tdF” parameter: If the alarm LED is on, an alarm has taken place.
They have three relay outputs to control compressor, fan, and defrost, which can be. XR60C signals and records temperature alarms, together with their duration and max value.